Uninterruptible Power supply. Digital Energy™. SitePro. 10 – 15 – 20 – 30 – 40 kVA. Vac CE / Series 8. GE Consumer & Industrial SA. SitePro, the most reliable Uninterruptible Power System available for data security and other demanding critical applications. GE Consumer & Industrial. Power Protection. Digital Energy™. SitePro. ®. Series UPS. Uninterruptible Power Supply 10 – kVA. GE imagination at work.
|Published (Last):||24 April 2012|
|PDF File Size:||14.88 Mb|
|ePub File Size:||1.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
Please carefully read the Operating Manual.
The meaning of the user parameters and their use is described below buttons performance is described to Section 7. In cases where the UPS needs to be powered down for maintenance purposes, the critical load must also be powered down during this time. A detailed report of the damage is necessary for any insurance claim.
The load is powered by the unit s supplying the parallel bus.
GE DIGITAL ENERGY SITEPRO VAC CESERIES 7 OPERATING MANUAL Pdf Download.
If optional cabinets and accessories are included with the UPS, please refer to those accompanying manuals for installation and operating instructions. The load must be transferred back to the UPS system. These signals are available either on connector J2- sub D, female 25 pin or terminal blocks X1. Inverter output fuses blown F5, F6, F7. The rectifier, powered by the mains, supplies the inverter and the battery-charger keeps the battery fully charged. Osborne Park WA May be reset by a service technician only.
This installation must be verified by trained personnel before the initial start-up.
To print the manual completely, please, download it. When the Inverter recovers, or the overload or short-circuit condition is corrected, the Witepro will be automatically transferred back to the Rectifiers Paralleled On The Same Battery A parallel system with a Common Battery for two or more UPS, requires a particular installation and adequate setting of some parameters, accessible only through passwordand can sitepeo only be done by a qualified GE engineer.
Parallel Control Bus Connection 4. Page 48 3 — Change the selected character. This unit will be powered on and connected to the parallel bus in order to share the load with each other’s.
GE Digital Energy SitePro 400 VAC CESeries 7 Operating Manual
Page 49 3 — Change to Functioning As Frequency Converter 4. Switch ON the mains voltage — As for the single version.
Options In Additional Cabinets A damaged UPS must never be installed or connected to mains or battery!
The UPS system and the critical load have to be completely powered down. The inverter converts the DC voltage in a new AC sine wave voltage with constant amplitude and frequency independently from the input Means that on d4 – Tuesday the SEM mode is active between Not following this procedure can cause protected loads to shut down!
Miscellaneous screen This screen displays: Now the control panel should indicate a normal situation No alarms.
Cooling air enters the cabinets through the air inlet grids located at the bottom and exhausted through the outlet on the roof.
To lift the cabinets, use sitepr forklift or lifting belts with spreader bars. The UPS output terminals must be supplied by the mains power through the sitelro bypass. Full voltage and current are always present at the battery terminals.
This product has been designed to respect the environment, using materials components respecting eco-design rules. Status load screen This screen displays: Page 3 Please carefully read the Operating Manual. If not already supplied separate mains inputsswitch-ON the mains power to the rectifier input.
SitePro UPS Vac / CE GE Consumer & Industrial August ppt download
This operation must be performed by trained personnel before the initial start-up ensure that the UPS installation is completely powered down. SitePro UPS provides reliable and robust protection for mission critical installations between IT and telecommunications, and infrastructure applications such as airports, hospitals, and financial companies.
UPS packing materials must be recycled in compliance with all applicable regulations. In case of any damage sustained during transport, immediately inform the carrier and contact your local Service Centre.
Please click here to enlarge. Open the front door and make sure that: The non-observance of the warnings reminding hazardous situations could result in human injury and equipment damages. Packing material recycling GE, in compliance with environment protection, use only environmentally friendly material.
This is the only printer-interface supported by the UPS. For parallel systems, the delivery also includes the bus control cables for inter- connecting the UPS modules. RX in Pin 5: Battery Location The UPS cabinet is free standing and normally does not require bolting to the floor. The meaning of the alarms on the free contacts in standard configuration default is the following: Page 66 For parallel systems perform the following procedure on each unit, starting from unit no.
Features Of Rpa Parallel System 3. Page 74 For parallel systems perform the following procedure on each unit, starting from unit no. The IEM mode for RPA can be freely programmed taking care of load changes during the day or degree of redundancy required. Service And Technical Support Fig.